Improper hook-up of Generator Sets AN/MJQ-16 and 18 may result in a
safety hazard to personnel and may damage equipment.
How to hook up AN/MJQ-16 and 18 Generator Sets requiring single phase
120 volts power.
1. Power selector switch on generator must be set to 120 Vac single
2. Connect shelter cable green wire to mechanical ground on metal
3. Connect black wire to terminal L1 (AC hot) and white wire to L3 (AC
4. Connect L3 to the mechanical ground connection with 8 AWG jumper.