44.) Replace with
a 40-amp single pole circuit breaker.
Connect new wiring to circuit breaker, indicator lamp,
neutral buss, and the ground buss as shown in wiring
saving the mounting screws for later usage.
(6) Bundle together no. 10 AWG black wire
(8) Install cover on power distribution panel .
Install raceway covers and raceway cover clips; and
990-3000), and no. 12 AWG green wire (6145-00-
install fluorescent lighting tubes removed in step (1).
9043811) (all type THW, stranded, approximately 12 feet
long) (fig. 43). Secure wires together, using twelve
(9) Fabricate 12-ft flexible cord (6145-00-295-
tiedown straps (MS3367-1) positioned approximately 12
0855) as shown in figure 45. Install flexible cord on
inches apart (fig. 43). Pull wire bundle into raceway
shelter wall behind engine lathe as shown in figure 46.
from power distribution panel to enclosure where duplex
Secure with four loop clamps (MS21333-41) installed
receptacle was removed. Terminate the three wires by
with existing screws. Connect flexible cord to cabinet of
connecting to receptacle (5935-01-038-7401) as shown
engine lathe with box connector (Appleton 15233) (fig.
45); terminate wiring
in accordance with engine lathe
mounting screws from the duplex receptacle.
(7) Remove existing circuit breaker installed
in position 11 of power distribution panel. (See figure
Section III. INSTALLATION IN ISO-2-1 SHELTER
Install blind rivet nuts in ISO-2-1 shelter,
unit 2 as follows:
Hand blind riveter (5120-00679-6523)
TYPE 1, CLASS 3 (8040-01102-2098),
is used for installing blind rivet nuts
(after installing blind rivet nuts) must
in accordance with MIL-N-47187.
have a curing time of 24 to 48 hours
before using any threaded fasteners.
Position floor mounted storage
(1) Mark and drill thirty-four 0.25-in. diameter
cabinets, support angles, work table,
holes in right and left wall to a maximum depth of 1.00
lathe mounting plate, first aid kit, and
fire extinguisher as shown in figures
compound as required and install thirty-four #10 blind
23 thru 28 and 30.
Use the equipment
rivet nuts (11021235-5).
mounting holes as templates for
location of blind rivet nuts. Positions
(2) Mark and drill thirty-three 0.41-in.
may be varied to drill into structural
diameter holes to a maximum depth of 1.50 inches in
members in the fixed floor.
right wall, fixed floor, deployed floor, and left deployed