CONNECTING POWER TO THE SHELTER
Tools and Special Tools
Electrical Repairers Tool Kit
General Mechanics Tool Kit
CMF 15 Series (2)
EXTERNAL GROUNDING OF SHELTER
Shelter is grounded through an externally connected power supply. Consult a qualiied electri-
cian for proper grounding procedures required for surrounding soil conditions.
External Grounding of Shelter.
Remove ground rod assembly (Figure 1, Item 5 and 6) from shelter BII box .
Remove slide hammer (WP 0065 00, Figure 2, Item 4) from Shelter BII box .
Ground rod location should permit ground cable lug to reach ground stud on power entry panel.
Drive ground rod (Figure 1, Item 6) into ground using slide hammer (WP 0065 00, Figure 2, Item 4).