REMOVING CABLE AND RECEPTACLE ASSEMBLY
Removing Cable and Receptacle Assembly.
Release power cables from Velcro straps (Figure 2, Item 2).
Release captive fasteners (Figure 2, Item 1) and reposition receptacles (Figure 2, Item 3) from operation
mode on hinged sidewall to transport mode on hinged end walls.
Position receptacles (Figure 2, Item 3) with power cables facing upward and secure with captive fasteners
(Figure 2, Item 1).
Repeat Steps 1 through 3 at opposite end of shelter.
REMOVING CEILING LIGHTS FROM HINGED ROOF
Ensure main circuit breaker and all other circuit breakers in circuit breaker panel are in
the OFF position. Serious shock hazards exist which could result in INJURY OR EVEN
DEATH to personnel.
Inhalation of phosphorous dust could cause SERIOUS INJURY to personnel. In an event
of lamp breakage, care must be taken in removal of broken glass fragments and white
phosphorous dust that may be dispersed within ixture.