3-18. Ground Rod/Strap - Inspect (Cont)
2. Check ground strap connection for security and
corrosion at terminal lug (5) on power entry panel
3. Check condition of ground using multimeter (7).
(Use TC 11-6).
Set multimeter (7) for AC voltage.
Place red lead on shelter.
Place black lead on ground strap.
0-5 volts, adequate ground;
Over 5 volts-poor ground, reinstall ground system.
END OF TASK