HIGH VOLTAGE exists in electrical system of shop. All electrical inspections,
repairs, or replacements will be performed with power OFF and only by a
qualified electrician. Serious shock hazards exist which could result in INJURY
OR EVEN DEATH to personnel.
CONNECTING PDB TO GENERATOR (IF NECESSARY)
Connecting PDB to generator is required only if power is not available. Only a
qualified electrician should attempt to connect PDB to generator.
PDB and pigtail are supplied by unit. Refer to TM 9-6150-226-13 and/or TM 9-
6150-226-23P for additional information. The following figure and steps are
specific to a 100 amp shelter.
BLUE OR ORANGE
2. Ensure pigtail is connected to PDB.
3. Connect pigtail wires to generator lugs by connecting black wire to lug L1, red wire to lug L2, blue or orange
wire to lug L3, and white and green wires to lug L0 on generator.