To prevent electrical shock or damage to equipment, ensure all circuit breakers at the
PDISE are set to the OFF position prior to connecting power cables to the ASLMS.
It is recommended that the ASLMS containers be grounded (grounding rod and strap not provided) when
in use. Ground lugs are located in the recessed areas at the front and rear of the containers. The
ASLMS system will be grounded through the generator or facility power. Operator should ensure the
power source is properly grounded.
Always connect both A/C and D/C connector cables to the rear of the FPU-12 (the side with step
plates) and the front of the FPU-8 (the side w/o step plates) prior to connecting to the PDISE.
This step will already be completed if containers are still connected.
2. Verify that the main breakers at the PDISE are set to the OFF position.
3. Connect the 150-foot power cables from the PDISE to the FPU-12 (bail bar side).
4. Set the main breakers to the ON position at the PDISE.
Setup of Overhead Lighting Fixture
9-FOOT DC CABLES
EPC must be erected before proceeding.
1. With the ASLMS containers joined together, EPC erected and power connected, remove the four
overhead lighting fixtures that are stowed inside the four compartments in the ceiling of the ASLMS