AUTHORIZED STOCKAGE LIST MOBILITY SYSTEM (ASLMS)
MODEL NUMBER FPU-8/12 PARTS (OD) P/N 15005002-001
MODEL NUMBER FPU-8/12 PARTS (DS) P/N 15005002-002
MODEL NUMBER FPU-8/12 BULK (OD) P/N 15005001-001
MODEL NUMBER FPU-8/12 BULK (DS) P/N 15005001-002
INSPECT, REPLACE, TEST
With the container connected to a proper power source, inspect receptacles for operability using a
standard power tool. If there is no power try to reset the reset button. If the reset button will not reset,
Electrical power must be disconnected before any electrical system work is performed to
prevent electrical shock, injury, or death (electrocution). Only trained and qualified
personnel (MOS 51R, 52C, 52E, or 52G) may perform maintenance or attempt to correct
electrical discrepancies on the electrical system.
Ensure all electrical power has been disconnected between the M40 PDISE and the FPU-12 external
power connection point.
Remove the GFCI cover plate (1) and retaining screws.
Remove the GFCI retaining screws (2).
Pull the receptacle (3) from the box to reveal the black, white and ground wire connections (4).
Remove the black (hot), white (neutral), and ground wire connections (4).
To install the new GFCI receptacle (3) reconnect the black, white and ground wire connections (4).