Clean metal parts with cleaning solvent (P-D-680) and dry
Inspect all parts of load centers for damage and replace as
Inspect the wiring covers and mounting brackets for dents,
cracks, breaks, loose or missing hardware and other defects.
(e) Tighten or replace loose or missing mounting hardware.
Straighten minor bends. Replace damaged or defective mounting brack-
ets, wiring covers, and flexible conduit.
(f) Test the wire for continuity. Disconnect each end of the
wire from the components to which it is attached as shown by the
wiring diagram (fig FO-1). Touch the test probes of a multimeter to
each end of the wire.
replace the wire.
Dangerous voltages, capable of causing death, are present in
this vehicle and the equipment provided in its tool load.
Use extreme caution when handling, testing, or adjusting any
The ceiling lights, bench grinder, and workbench receptacles
are supplied with power by 120-volt, single-phase circuit.
Wiring for each circuit in this system must be replaced
Refer to the wiring diagrams (fig FO-1) when
testing and replacing wiring in the individual circuits.
c. Assembly and Installation. Refer to figures 9 through 15 to
reassemble, install and reconnect electrical components.